We’ve proudly represented the very best Atlanta has to offer in superior service for 50 years. In that time, we’ve accumulated all it takes and more to bring you the best emergency heating and air conditioning repair services possible. Story after story, we deliver smiles! If you’re looking for a reliable company that provides 24-hour AC repair, don’t hesitate to contact us right away—770-913-6412!
If your compressor doesn’t have an overload button and you hear it humming or buzzing, poke a screwdriver or stick down through the top grille and try to spin the fan blades clockwise. If doing this gives the fan enough of a boost to get it going, the unit has a faulty capacitor that must be replaced. See How to Test and Replace an AC Run Capacitor, above.
When central air conditioning service fails during a heat spell, you may have to wait days for an HVAC repair technician or a ac contractor to show up, and you’ll probably pay at least several hundred for the repair. But if you’re comfortable working around electricity and are willing to spend about $50 on parts, you can probably repair your air conditioning service yourself in about two hours and save about $225 on parts markup and labor.
If the condenser coils are clogged, the compressor can overheat and shut down. You’ll experience intermittent periods of minimal cooling, followed by no cooling. Even if you’re “sure” the condenser coils are clean, clean them again. Turn off the power. Flip the air conditioning service and furnace circuit breakers in your main electrical panel to the “Off” position. Next, turn off the power switch right at the furnace or air handler. Then yank the disconnect block (Photo 1) and clean the condenser coils (Photo 2). If the air conditioning service still doesn’t work properly after you’ve cleaned the condenser coils, installed a new filter and opened all the supply vents, proceed with the following repairs.
Before opening the electrical cover on the A/C unit, be sure to shut off all power to the compressor unit and the indoor furnace or air handler, and verify that it is off. Note that this may mean shutting off a circuit breaker that serves the furnace and air handler, and then, near the compressor, pulling out the disconnect block (or shutting off the 220-volt power) to the outdoor compressor.